Maintenances and incidents regarding our services, networks and datacenters can be followed here.
In order to upgrade one peering router in AMS1, we will isolate a router and reload it.
Impact : No impact on traffic from / to AS12876 as we have enough capacity on other peering routers.
Start: 09.16.2019: 07.00am UTC End: 09.16.2019: 09.00am UTC
We will undertake a preventive maintenance on our refrigeration units on DC3.
Impact: Minor loss of redundancy, no customer impact.
START: 10-Oct-2019 0630Z 0830LT
END: 11-Nov-2019 0330Z 0530LT
DC3 electrical generators - Redundancy test of DC3 electrical generators
Location : DC3 What is done : As part of the preventive maintenance of the Datacenter, we will proceed to a redundancy test of the Datacenter infrastructure. The operation consists of simulating a power failure on the MVLBs and validating the electrical load recovery and working on generator for 4 hours. Impact : no impact on client servers
Duration : 4 hours
Upgrade over the RPN network between AMS1 and DC3
Network supplier must perform maintenance on his Network. Maintenance window is from October 26th, 2019 at 10:00 pm UTC to October 27th, 2019 at 4:00 am UTC. The expected Impact length is 6 hours at the maximum, during the maintenance window
Impact : Downtime on the rpn network between AMS1 and DC3
It will last : 6 hours
DC3 - Maintenance of distribution pumps
Location : DC3 Substation-A, Substation-B, Substation-C
What is done : We will perform the semi-annual maintenance of the distribution pumps. Operations will be performed by our maintainer under our permanent supervision, according to the following previsional schedule:
Wednesday November 6th: Sub-station A
Thursday November 7th Sub-station B
Friday November 8th Sub-station C
Substations A and B supply the chilled water network of the computer halls. Substation C supplies the chilled water network of the operators halls and the air handing units.
Impact : no impact for customers
Duration : 3 Days
DC3 - Preventive maintenance of air handling units
Location : DC3
What is done : preventive maintenance of air handling units will be performed on the whole site.
Thursday November 12th: Room 01 and 02
Wednesday November 13th: Room 03 and 04
Thursday November 14th: TGBT A and B
Friday November 15th: TGBT C and D
Monday November 18th: TGBT F1 and F2
Impact : loss of redundancy during the preventive maintenance of a TGBT air handling unit. No impact on TGBT cooling.
Duration : 5 Days