Scheduled maintenance is currently in progress. We will provide updates as necessary.
Posted Feb 08, 2021 - 10:01 CET
We will do the curative maintenance of the pumps unit of chillers 5.
The 2020 thermography report shows a tightening fault on a circuit breaker. This one will be replaced.
During maintenance, the chiller GF5 will be stop. The chillers GF4 and GF6 will be on setpoint 1. Operations will be performed by our maintainer.
Since only one refrigeration unit is switched off at the same time, only the redundancy is degraded. In the event of a failure of a chiller operating in the same substation as the maintenance one, our maintainer will have the possibility to restart the chiller quickly or, in case of failure, to mix the chilled water networks SSA and SSB.
Posted Feb 04, 2021 - 11:43 CET
This scheduled maintenance affected: Dedibox - Datacenters (DC3).